Confidential Client – B42 Boiler Upgrades
This Fortune 500 Pharmaceutical company’s B42 in Spring House, PA was supported by three (3) boilers equipped with burners that had become obsolete. Additionally, one of the burners failed due to consistently operating at extremely low turn-down, below what the equipment was designed to support. These boilers supported several central utilities critical to building operation, including humidification, hot water reheat, lab hot water and domestic hot water. Cyma Builders furnished and installed new Johnson Burners on the boilers during controlled shutdown to limit operation risk to the R&D operations ongoing in the building. Additionally, new a new lead lag control system was added to ensure proper boiler run-time and sequenced operation.